Vapour-compression refrigeration or vapor-compression refrigeration system (VCRS), in which the refrigerant undergoes phase changes, is one of the many refrigeration cycles and is the most widely used method for air-conditioning of buildings and automobiles. It is also used in domestic and commercial refrigerators, large-scale warehouses for chilled or frozen storage of foods and meats, refrigerated trucks and railroad cars, and a host of other commercial and industrial services. Oil refineries, petrochemical and chemical processing plants, and natural gas processing plants are among the many types of industrial plants that often utilize large vapor-compression refrigeration systems. Cascade refrigeration systems may also be implemented using 2 compressors.
Refrigeration may be defined as lowering the temperature of an enclosed space by removing heat from that space and transferring it elsewhere. A device that performs this function may also be called an air conditioner, refrigerator, air source heat pump, geothermal heat pump, or chiller (heat pump).
Vapor-compression uses a circulating liquid refrigerant as the medium which absorbs and removes heat from the space to be cooled and subsequently rejects that heat elsewhere. Figure 1 depicts a typical, single-stage vapor-compression system. All such systems have four components: a compressor, a condenser, a thermal expansion valve (also called a throttle valve or metering device), and an evaporator. Circulating refrigerant enters the compressor in the thermodynamic state known as a saturated vapor and is compressed to a higher pressure, resulting in a higher temperature as well. The hot, compressed vapor is then in the thermodynamic state known as a superheated vapor and it is at a temperature and pressure at which it can be condensed with either cooling water or cooling air flowing across the coil or tubes. This is where the circulating refrigerant rejects heat from the system and the rejected heat is carried away by either the water or the air (whichever may be the case).
The condensed liquid refrigerant, in the thermodynamic state known as a saturated liquid, is next routed through an expansion valve where it undergoes an abrupt reduction in pressure. That pressure reduction results in the adiabatic flash evaporation of a part of the liquid refrigerant. The auto-refrigeration effect of the adiabatic flash evaporation lowers the temperature of the liquid and vapor refrigerant mixture to where it is colder than the temperature of the enclosed space to be refrigerated.
The cold mixture is then routed through the coil or tubes in the evaporator. A fan circulates the warm air in the enclosed space across the coil or tubes carrying the cold refrigerant liquid and vapor mixture. That warm air evaporates the liquid part of the cold refrigerant mixture. At the same time, the circulating air is cooled and thus lowers the temperature of the enclosed space to the desired temperature. The evaporator is where the circulating refrigerant absorbs and removes heat which is subsequently rejected in the condenser and transferred elsewhere by the water or air used in the condenser.
To complete the refrigeration cycle, the refrigerant vapor from the evaporator is again a saturated vapor and is routed back into the compressor. Over time, the evaporator may collect ice or water from ambient humidity. The ice is melted through defrosting. The water from the melted ice or the evaporator then drips into a drip pan, and the water is carried away by gravity or by a pump.
The selection of working fluid has a significant impact on the performance of the refrigeration cycles and as such it plays a key role when it comes to designing or simply choosing an ideal machine for a certain task. One of the most widespread refrigerant is "Freon". Freon is a trade name for a family of haloalkane refrigerants manufactured by DuPont and other companies. These refrigerants were commonly used due to their superior stability and safety properties: they were not flammable at room temperature and atmospheric pressure, nor obviously toxic as were the fluids they replaced, such as sulfur dioxide. Haloalkanes are also an order(s) of magnitude more expensive than petroleum derived flammable alkanes of similar or better cooling performance.
Unfortunately, chlorine- and fluorine-bearing refrigerants reach the upper atmosphere when they escape. In the stratosphere, substances like CFCs and HCFCs break up due to UV radiation, releasing their chlorine free radicals. These chlorine free radicals act as catalysts in the breakdown of ozone through chain reactions. One CFC molecule can cause thousands of ozone molecules to break down. This causes severe damage to the ozone layer that shields the Earth's surface from the Sun's strong UV radiation, and has been shown to lead to increased rates of skin cancer. The chlorine will remain active as a catalyst until and unless it binds with another particle, forming a stable molecule. CFC refrigerants in common but receding usage include R-11 and R-12.
Newer refrigerants with reduced ozone depletion effect such as HCFCs (R-22, used in most homes today) and HFCs (R-134a, used in most cars) have replaced most CFC use. HCFCs in turn are being phased out under the Montreal Protocol and replaced by hydrofluorocarbons (HFCs), that do not contain chlorine atoms. Small example of common HFCs in current use: R-410A (which is itself a blend of other HFCs: R-32 and R-125) ; designed to be a drop-in replacement for R-22 in existing installations) and R-404A (blend of HFCs: R-125, R-134a, and R-143a, and was developed as a substitute refrigerant for R-502 and R-22). However, CFCs, HCFCs, and HFCs all have very large global warming potential (GWP).
More benign refrigerants are currently the subject of research, such as supercritical carbon dioxide, known as R-744. These have similar efficiencies compared to existing CFC- and HFC-based compounds, and have many orders of magnitude lower global warming potential. General industry and governing body push is toward more GWP friendly refrigerants. In industrial settings ammonia, as well gasses like ethylene, propane, iso-butane and other hydrocarbons are commonly used (and have own R-x customary numbers), depending on required temperatures and pressures. Many of these gases are unfortunately flammable, explosive, or toxic; making their use restricted (i.e. well controlled environments by qualified personnel, or very small amount of refrigerant used). HFOs which can be considered to be HFC with some carbon-carbon bonds being double bounds, do show promise of lowering GWP very low to be of no further concern. In the meantime various blends of existing refrigerants are used to achieve required properties and efficiency, at reasonable cost and lower GWP.
The thermodynamics of the vapor compression cycle can be analyzed on a temperature versus entropy diagram as depicted in Figure 2. At point 1 in the diagram, the circulating refrigerant enters the compressor as a saturated vapor. From point 1 to point 2, the vapor is isentropically compressed (compressed at constant entropy) and exits the compressor as a superheated vapor. Superheat is the amount of heat added above the boiling point.
From point 2 to point 3, the vapor travels through part of the condenser which removes the superheat by cooling the vapor. Between point 3 and point 4, the vapor travels through the remainder of the condenser and is condensed into a saturated liquid. The condensation process occurs at essentially constant pressure.
Between points 4 and 5, the saturated liquid refrigerant passes through the expansion valve and undergoes an abrupt decrease of pressure. That process results in the adiabatic flash evaporation and auto-refrigeration of a portion of the liquid (typically, less than half of the liquid flashes). The adiabatic flash evaporation process is isenthalpic (occurs at constant enthalpy).
Between points 5 and 1, the cold and partially vaporized refrigerant travels through the coil or tubes in the evaporator where it is totally vaporized by the warm air (from the space being refrigerated) that a fan circulates across the coil or tubes in the evaporator. The evaporator operates at essentially constant pressure and boils off all available liquid there after adding 4-8 kelvins of superheat to the refrigerant in order to make sure the liquid has evaporated completely. This is a safeguard for the compressor, as it cannot pump liquid. The resulting refrigerant vapor returns to the compressor inlet at point 1 to complete the thermodynamic cycle.
The above discussion is based on the ideal vapor-compression refrigeration cycle which does not take into account real world items like frictional pressure drop in the system, slight internal irreversibility during the compression of the refrigerant vapor, or non-ideal gas behavior (if any).
The most common compressors used in refrigeration are reciprocating and scroll compressors, but large chillers or industrial cycles may use rotary screw or centrifugal compressors. Each application prefers one or another due to size, noise, efficiency, and pressure issues. Compressors are often described as being either open, hermetic, or semi-hermetic, to describe how the compressor and/or motor is situated in relation to the refrigerant being compressed. Variations of motor/compressor types can lead to the following configurations:
Typically in hermetic, and most semi-hermetic compressors (sometimes known as accessible hermetic compressors), the compressor and motor driving the compressor are integrated, and operate within the refrigerant system. The motor is hermetic and is designed to operate, and be cooled by, the refrigerant being compressed. The obvious disadvantage of hermetic motor compressors is that the motor drive cannot be maintained in situ, and the entire compressor must be removed if a motor fails. A further disadvantage is that burnt out windings can contaminate whole refrigeration systems requiring the system to be entirely pumped down, and the refrigerant replaced.
An open compressor has a motor drive which is outside of the refrigeration system, and provides drive to the compressor by means of an input shaft with suitable gland seals. Open compressor motors are typically air-cooled and can be fairly easily exchanged or repaired without degassing of the refrigeration system. The disadvantage of this type of compressor is a failure of the shaft seals, leading to loss of refrigerant.
Open motor compressors are generally easier to cool (using ambient air) and therefore tend to be simpler in design and more reliable, especially in high pressure applications where compressed gas temperatures can be very high. However the use of liquid injection for additional cooling can generally overcome this issue in most hermetic motor compressors.
Reciprocating compressors are piston-style, positive displacement compressors.
Rotary screw compressors are also positive displacement compressors. Two meshing screw-rotors rotate in opposite directions, trapping refrigerant vapor, and reducing the volume of the refrigerant along the rotors to the discharge point.
Small units are not practical due to back-leakage but large units have very high efficiency and flow capacity.
Centrifugal compressors are dynamic compressors. These compressors raise the pressure of the refrigerant by imparting velocity or dynamic energy, using a rotating impeller, and converting it to pressure energy.
Scroll compressors are also positive displacement compressors. The refrigerant is compressed when one spiral orbits around a second stationary spiral, creating smaller and smaller pockets and higher pressures. By the time the refrigerant is discharged, it is fully pressurized.
Axial-flow compressor of a jet engine
In order to lubricate the moving parts of the compressor, oil is added to the refrigerant during installation or commissioning. The type of oil may be mineral or synthetic to suit the compressor type, and also chosen so as not to react with the refrigerant type and other components in the system. In small refrigeration systems the oil is allowed to circulate throughout the whole circuit, but care must be taken to design the pipework and components such that oil can drain back under gravity to the compressor. In larger more distributed systems, especially in retail refrigeration, the oil is normally captured at an oil separator immediately after the compressor, and is in turn re-delivered, by an oil level management system, back to the compressor(s). Oil separators are not 100% efficient so system pipework must still be designed so that oil can drain back by gravity to the oil separator or compressor.
Some newer compressor technologies use magnetic bearings or air bearings and require no lubrication, for example the Danfoss Turbocor range of centrifugal compressors. Avoiding the need for oil lubrication and the design requirements and ancillaries associated with it, simplifies the design of the refrigerant system, increases the heat transfer coefficient in evaporators and condensers, eliminates the risk of refrigerant being contaminated with oil, and reduces maintenance requirements.
In simple commercial refrigeration systems the compressor is normally controlled by a simple pressure switch, with the expansion performed by a capillary tube or simple thermostatic expansion valve. In more complex systems, including multiple compressor installations, the use of electronic controls is typical, with adjustable set points to control the pressure at which compressors cut in and cut out, and temperature control by the use of electronic expansion valves.
In addition to the operational controls, separate high-pressure and low-pressure switches are normally utilised to provide secondary protection to the compressors and other components of the system from operating outside of safe parameters.
In more advanced electronic control systems the use of floating head pressure, and proactive suction pressure, control routines allow the compressor operation to be adjusted to accurately meet differing cooling demands while reducing energy consumption.
The schematic diagram of a single-stage refrigeration system shown in Figure 1 does not include other equipment items that would be provided in a large commercial or industrial vapor compression refrigeration system, such as:
In most of the world, the cooling capacity of refrigeration systems is measured in watts. Common residential air conditioning units range in capacity from 3.5-18 kilowatt. In a few countries it is measured in "tons of refrigeration", with common residential air conditioning units from about 1 to 5 tons of refrigeration.
|Refrigeration application||Short descriptions||Typical refrigerators used|
|Domestic refrigeration||Appliances used for keeping food in dwelling units||R-600a, R-134a, R-22,|
|Commercial refrigeration||Holding and displaying frozen and fresh food in retail outlets||R-134a, R-404A, R-507|
|Food processing and cold storage||Equipment to preserve, process, and store food from its source to the wholesale distribution point||R-123, R-134a, R-407C, R-410A, R-507|
|Industrial refrigeration||Large equipment, typically 25 kW to 30 MW, used for chemical processing, cold storage, food processing, building, and district heating and cooling||R-123, R-134a, R-404A, R-407C, R-507, R-717|
|Transport refrigeration||Equipment to preserve and store goods, primarily foodstuffs, during transport by road, rail, air, and sea||R-134a, R-407C, R-410A|
|Electronic cooling||Low-temperature cooling of CMOS circuitry and other components in large computers and servers||R-134a, R-404A, R-507|
|Medical refrigeration||R-134a, R-404A, R-507|
|Cryogenic refrigeration||Ethylene, propane, nitrogen, helium|
Many systems still use HCFC refrigerants, which contribute to depletion of the Earth's ozone layer. In countries adhering to the Montreal Protocol, HCFCs are due to be phased out and are largely being replaced by ozone-friendly HFCs. However, systems using HFC refrigerants tend to be slightly less efficient than systems using HCFCs. HFCs also have an extremely large global warming potential, because they remain in the atmosphere for many years and trap heat more effectively than carbon dioxide.
With the ultimate phasing out of HCFCs already a certainty, alternative non-haloalkane refrigerants are gaining popularity. In particular, once-abandoned refrigerants such as hydrocarbons (butane for example) and CO2 are coming back into more extensive use. For example, Coca-Cola's vending machines at the 2006 FIFA World Cup in Germany used refrigeration utilizing CO2.Ammonia (NH3) is one of the oldest refrigerants, with excellent performance and essentially no pollution problems. However, ammonia has two disadvantages: it is toxic and it is incompatible with copper tubing.
In 1805, the American inventor Oliver Evans described a closed vapor-compression refrigeration cycle for the production of ice by ether under vacuum. Heat would be removed from the environment by recycling vaporized refrigerant, where it would move through a compressor and condenser, and would eventually revert to a liquid form in order to repeat the refrigeration process over again. However, no such refrigeration unit was built by Evans.
In 1834, an American expatriate to Great Britain, Jacob Perkins, built the first working vapor-compression refrigeration system in the world. It was a closed-cycle that could operate continuously, as he described in his patent:
His prototype system worked although it did not succeed commercially.
A similar attempt was made in 1842, by American physician, John Gorrie, who built a working prototype, but it was a commercial failure. American engineer Alexander Twining took out a British patent in 1850 for a vapor compression system that used ether.
The first practical vapor compression refrigeration system was built by James Harrison, a British journalist who had emigrated to Australia. His 1856 patent was for a vapor compression system using ether, alcohol or ammonia. He built a mechanical ice-making machine in 1851 on the banks of the Barwon River at Rocky Point in Geelong, Victoria, and his first commercial ice-making machine followed in 1854. Harrison also introduced commercial vapor-compression refrigeration to breweries and meat packing houses and, by 1861, a dozen of his systems were in operation in Australia and England.
The first gas absorption refrigeration system using gaseous ammonia dissolved in water (referred to as "aqua ammonia") was developed by Ferdinand Carré of France in 1859 and patented in 1860. Carl von Linde, an engineering professor at the Technological University Munich in Germany, patented an improved method of liquefying gases in 1876. His new process made possible using gases such as ammonia, sulfur dioxide , and methyl chloride (CH3Cl) as refrigerants and they were widely used for that purpose until the late 1920s.